|Capacity (KLD/MLD)||100 KLD|
|Installation Type||Containerized Plug & Play|
|Feed Flow Rate(m3/day or m3/hr)||51-100 m3/day|
|Water Pump Power||0.5 KW|
|Treatment Technology||Membrane Bioreactor(MBR)|
|I Deal In||New Only|
|Material Of Construction||Mild Steel|
|Air Blower Count||2 Blowers|
|Air Blower Power||0.25 KW|
|Country of Origin||Made in India|
|Water Source Type||Sea Water|
|Automation Grade||Fully Automatic|
|Capacity||10 L/h to 5000 L/h|
|Installation/Civil Work||Installation Available|
|For Conveyor||05 Hp|
Owing to our expertise in the domain of manufacturing and supplying of Sea Water Treatment Plant.
|Minimum Order Quantity||1 piece|
|Capacity (KLD)||1 KLD - 50 KLD|
|Feed Flow Rate(m3/day or m3/hr)||1 m3/day - 50 m3/day|
|Application Industry||Residential & Commercial Building|
|Treatment Technique||Clarifier, Fluidized Aerated Reactor|
|Deliver Type||Outside India, PAN India|
|Material Of Construction||Stainless Steel|
|I Deal In||New Only|
|Treatment Stages||Primary Treatment|
|Rated Power||2.5 Kw|
What differentiates our organization from others is our expertise in the domain of manufacture and supply of Packaged Sewage Treatment Plant.
1. Preliminary Treatment
The influent sewage water passes through a bar screen to remove all the large objects like cans, rags, sticks, plastic packets etc. which are carried in the sewage stream.
2. Secondary Treatment
a. Anaerobic Zone-
The first stage of PSTP is an oxygen-depleted anaerobic zone in which the solids in raw sewage gets settled while allowing the scum to float on the surface. It is a zone in which the settled sludge is stabilized by anaerobic digestion.
b. Anoxic Zone-
The sewage then enters the anoxic zone in which denitrification of the wastewater stream is accomplished by returning the activated sludge from the final sedimentation zone to the anoxic zone; wherein dissolved oxygen levels are maintained approximately as 0.2 to 0.5 mg/l. In the denitrification process, anoxic microbes break down to the existing nitrates, this results in the release of inert nitrogen gas into the atmosphere.
c. Aeration Zone-
The sewage from the solid separation zone flows into the aeration zone. Air is diffused with the help of air blowers which encourages the growth of bacteria cultures in and around the floating plastic media added in the aeration zone. The MBBR media provides the extended surface area for the growth of microorganisms.
d. Sedimentation Zone-
The next step of treatment involves the sedimentation zone where organic waste is settled. The settled waste in the bottom of the tank is pumped back to the anoxic zone as a return sludge, which is done to ensure that the quality of effluent must pass the stipulated sewage parameters.
3. Tertiary Treatment System:
The secondary treated sewage is then passed through the Pressure Sand Filter and Activated Carbon Filter for the removal of suspended solids (TSS), color, and odor. The treated water is then disinfected using sodium hypochlorite before it is reused.
We are stp plant manufacturers, we supply various types of sewage treatment plants in India Residential sewage treatment plant , MBBR sewage treatment plant , mbr sewage treatment plant , Industrial sewage treatment plant, household sewage treatment plant , SBR sewage treatment plant , commercial sewage treatment plant , Domestic sewage treatment plant and domestic sewage treatment system.